dixell. DEFAULT SETTING VALUES. تا تا تست ه تا تن تا نا م ع. XR60C signals and records temperature alarms, together with their duration and max. View and Download Emerson Dixell XR60C installing and operating instructions online. Digital controller with defrost and fans management. Dixell XR60C. Dixell Srl reserves the right to change the composition of its products, even without or faulty operation send the instrument back to the distributor or to Dixell Srl.
|Published (Last):||16 September 2004|
|PDF File Size:||4.37 Mb|
|ePub File Size:||5.16 Mb|
|Price:||Free* [*Free Regsitration Required]|
The fan control mode is selected by means of the “FnC” parameter:. In xr660c of failure or faulty operation send the instrument back to the distributor or to “Dixell. Got it, continue to print. Don’t have an account? Fit the probe where it is not accessible by the End User. Comments to this Manuals Your Name. In case of fault in the thermostat probe the start and stop of the compressor are timed through. xr660c
Page of 4 Go. Enter text from picture: Check the supply voltage is correct before connecting the instrument. Ensure that the wires for probes, loads and the power supply are separated and far enough. Do not expose to water or moisture: Xd60c and immediately release the SET key or wait for 5 seconds to. This is used to make sure circulation of air only. On the display the following message is shown: Flexible machine integration through communications 50 pages.
After defrost, there is a timed fan delay allowing for drip time, set by means of the “Fnd”. Consider the maximum current which can be applied to each relay see Technical Data.
electronic controller DIXELL XR60C 379983
To see the kind of alarm, the max min. Don’t show me this message again. An additional parameter “FSt” provides the setting of temperature, detected by the evaporator. Other parameters are used to control the.
The instrument must not be opened. Hold the SET key pressed for more than 3s, while the recorded alarm is displayed. Push and immediately release the SET key: The instrument is provided with screw terminal block to connect cables with a cross section up nPS Pressure switch number: This manual also for: Then the instrument displays the temperature once again.
Two defrost modes are available through the “tdF” parameter: This function managed by the Fct parameter is designed to avoid short cycles of fans, that. If the alarm LED is on, an alarm has taken place.
EMERSON DIXELL XR60C INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
Add to my manuals Add. To confirm the dixeell, the “rSt” message starts blinking and the normal temperature. To display target set point; in programming mode it selects a parameter or confirm an.
The instrument shall not be used for purposes different from those described hereunder. XR60C signals and records temperature alarms, together with their duration and max value. Each LED function is described in the following table.
At the end of defrost dripping time is started, its length is set in the FSt parameter. They have three relay outputs to control compressor, fan, and defrost, which can be. In case of applications in industrial environments, the use of mains filters dixdll mod. Dixell Srl reserves the right to change the composition of its products, even without notice. To print the manual completely, please, download it.
Unidrive hs series; unidrive m series. To see the last temperature alarm happened; in programming mode it browses the. Digital controller with defrost sixell fans management. By pressing ‘print’ button you will print only current page. The instrument is fully configurable. This manual is part of the product and should be kept near the instrument for easy and quick.
Universal variable speed ac drive for induction and permanent magnetmotors pages.